The Rise of leakage current in Electrical Power Distributions are quite dangerous, resulting in Electrical hazards. Leakage Current are due to deterioration of insulations, negligence of wire man, bad wiring, and inferior / substandard usage of Electrical Materials, aging or endurance of Electrical environment.
First and foremost importance should be given for the proper Earthing of Electrical Network System. The Earth Leakage Current are very low and are sensitive leakage current can be detected by Ground Fault Monitoring System. GFMS detects the leakage current in the circuit and isolate the power supply by switching off the tripping device – Contactor.
Micro Controller based compact Design.
8 Character 2 Line LCD Display with Backlit.
True RMS Measurement of Leakage Current.
Continuous Monitoring and Display of Set value and Measured value of Leakage Current.
Immune to external disturbances like harmonics and transients.
Test and Reset facility.
CBCT Connection monitoring facility.
Trip Circuit Failure Indication.
Consistent reliability with accuracy.
Temper proof Polycarbonate cover in the front with locking facility.
Optional RS 485 communication port.
Data processing facilities
Health Care Facilities
Office building & hotels
Automated Industrial Plants
Fire hazard areas
Current Setting Range
300 mA to 12 Amps. In step - 300mA / 500mA / 750mA / 1.00A / 1.25 / 1.50 / 1.75 / 2.50 / 3.00 / 4.00 / 5.00 / 6.00 / 7.00 / 8.00 / 9.00 / 10.00 / 11.00 / 12.00 Amp. With 1 mA resolution upto 1A and 10mA upto 12A Accuracy - ± 2 %
0.0 Second top 5 Seconds in step of 0.05 Sec
Instantaneous Tripping Time
less than 35 msec.
Core Balance Current Transformer
Moulded case CBCT with open circuit detection.
RS. 485 (Optional)
Potential Free contact
2 Change Over Contact – for Tripping and Alarm.
-5 to 55 °C.
IEC 60255 / IEC 755
IEC-755 Clause 8.3 Verification of operating characteristics
Insulation test IEC-60255 , insulation resistance test as per IEC 60255 – CL- 5 & 7
Dielectric test as per IEC-60255-CL-5&6
Impulse voltage test as per IEC-60255-CL-5&8
230V 50 Hz
Measuring accuracy with closed transformer
with split transformer
30 mA to 9999mA
Local measuring point
10mA to 11A
Time delay setting
to 99 sec.
Remote measuring point
30mA to 11A
one relay for 16 channels 2 pcs change
over contacts max 30 VAC 1.25A